Continuous monitoring of CO2 in fermentation rooms and bottling area.
Areas of concern for high levels of Carbon dioxide (CO2) in breweries include the fermentation room and bottling area. During fermentation a significant amount of CO2 is generated and depending on the setup, may be ventilated or captured for use. Any CO2 that escapes can collect in low lying areas, forming potentially hazardous pools of gas that can build up and displace Oxygen (O2). Levels of CO2 should be checked prior to workers going into the vats to clean them. Being odourless and colourless, the presence of CO2 is not known until symptoms of exposure are experienced, unless gas detection equipment is used.
Using Critical Environment Technologies Canada Inc. (CETCI)’s QCC Quad Channel Controller with a cGas Detector CO2 Transmitter is the solution. The placement of the transmitter inside the fermentation room and the bottling area provides continuous monitoring for potential leaks of Carbon dioxide. The QCC Controller with a top mounted strobe mounted outside the room door provides a status of the air quality conditions inside the room prior to entry. If a CO2 leak is detected the top mounted strobe will activate and an audible alarm will sound. The designated relays in the QCC will activate a preset response, such as turning on a remote alarm device, actuating the mechanical ventilation system and/or triggering another set response as required.
Typical CO2 Fermentation Room Monitoring System
Note: The cGas Detector CO2 transmitter is available with analog output (CGAS-A-CO2-5%) or Modbus output (CGAS-D-CO2-5%).
Inside the fermentation room, there should be a cGas Detector with an infrared CO2 sensor mounted on the wall at the breathing zone height (4 - 6 feet from the floor). It should be close to the fermentation tanks where the possibility of a Carbon dioxide leak is most likely to occur. The measurement range for Carbon Dioxide is 0 - 5% volume. With the optional splash guard installed, the enclosure is water tight (IP54 rated) and will withstand water spray or wash down applications.
During the bottling process CO2 is used to pre-fill each bottle before it is filled with beer. Another cGas Detector with a CO2 infrared sensor should be mounted in the bottling area to monitor and protect workers on the bottling line.
The QCC Quad Channel Controller with a top mounted strobe should be mounted outside the fermentation room entry door. It will interface to the cGas Detector inside the room and will display the target gas levels for viewing prior to entering the room. The QCC is pre-programmed and field adjustable. Functions that can be set include relay assignment, time delays, logic control, sensor types and ranges, alarm set points, etc. There is a 4-line x 20 character backlit LCD display that actively scrolls through the programmed channels and displays the gas name, concentration and alarm status. The QCC should be configured to set off alarms and activate the exhaust ventilation system, shut down the chillers or other alarm procedures as appropriate when a leak is detected. The QCC can accept inputs from up to 4 transmitters, using either an analog (4 - 20 mA) signal and/or Modbus® RS-485 digital communication, making it the ideal central controller for any additional gas detectors that may be needed throughout the winery.
Remote visual and audible alarm devices such as the Remote Strobe / Horn (RSH-24V) should be set up inside each room and if there is another entrance to the room, a QCC-RDM Remote Display Module should be mounted outside the door of that entrance, to provide visual confirmation of gas level readings prior to entering the room.